I received a photo of the construction of the firewood stove and chimney from the DIY construction customer!
I received a photo from a customer in okayama.
It seems that he decided to put the wood stove away during the renovation.
I went all the way to the warehouse in Takarazuka City, Hyogo Prefecture to pick up the chimney and the wood stove.
It was a pleasure to talk with you.
It's really nice to be able to connect with various customers even though it's an online shop.
When the installation was completed in the middle of summer and they tried to burn it after completion, it seems that there was a big backlash from the family (laughs)
Have you finished setting fire safely?
I wish you all the best.
MG500 made in Greece
I was persuaded to take the last one of the exhibits.
Therefore, there are currently no exhibits in the warehouse.
I can't show you the actual product until it arrives in November.
There was a problem with the width of the bottom ash tray.
I purchased an extra ash pan for the next shipment, so I will send you a new one when it arrives!
Please wait for a while
The tiled roof of the shed is penetrated by aluminum-based silicon flashing.
Since it is an aluminum base, it can handle the unevenness of the tiled roof to some extent, but the width was not enough.
The missing part is added with the flushing sheet sold by the piece.
The butyl tape is closely attached to the back side, so it is convenient to stick anywhere.
But as far as I can see from the picture, the correct answer is to put it under the black sheet above.
Since it's a shed, the water from above doesn't flow except during a storm, so I don't think there's a problem...
What is that black sheet about 30cm from the wall?
This is also not our store, but it seems that a flushing sheet can be used as a substitute.
It may be a little lacking in support from the wall.
I think it would be better to put another wall bracket etc. to prevent left and right shaking.
Especially during a typhoon, it takes a lot of force, so I think it would be better to reinforce it.
It covers the sloped ceiling well.
Is this from our shop?
I do not know.
A heat shield is firmly attached to the single chimney.
It is now possible to reduce the 45 cm clearance to combustibles by half to 22.5 cm.
It seems that the main body is a little too close to the back, so we recommend that you measure the temperature of the inner surface of the furnace wall once.
Completion of construction does not mean completion.
After that, seeing the inside will lead to safety.
Be careful not to catch fire!